Pioneer Power Group performs coordination studies by preparing time current curves for each unique branch of a distribution system. By analyzing the tripping curves for each overcurrent protective device, Pioneer is able to recommend the best possible settings to:
Ensure outages are minimized during abnormal conditions such as faults and overloads within the distribution system
Ensure equipment is properly protected
Minimize arc-flash incident energy levels at key equipment locations
The recommended protective device settings are shown on each time current curve along with a single line diagram of the portion of the system applicable to the curve. All protective device settings are summarized in one, comprehensive settings table at the end of each report. This table is organized in a way that allows readers to quickly and easily identify settings that are required during start-up and commissioning.
Coordination Study Company
Pioneer Power Group is one of the largest engineering teams focused solely on electrical systems studies. With relevant, deep technical knowledge we can help offer valuable insight by performing short circuit, coordination, and arc flash studies.
Why Is a Coordination Study Needed?
Electrical coordination studies are performed to ensure the safety of the system, personnel, and property. These studies evaluate the protective devices and are essential to increase system reliability and continuity of service. Coordination studies are also important in determining proper protective device settings to ensure the system is protected and reduce arc flash hazards.
At Pioneer Power Group, we make coordination studies easy for our customers. Upon receiving a one-line diagram of the system, our engineers put together a data request form outlining all the information needed to complete the study. This data is used ...
"Late in the project I realized I could not energize my equipment without the coordination study's protective device settings. No one expected to complete that study in 2 weeks, but Pioneer Power Group coordinated closely with us, completed the study in less than 2 weeks, and allowed us to maintain our schedule and workflow."